Input (english units with metric equivalents displayed):
ceiling type (open/dropped)
side wall type (curtain/solid)
wall and ceiling R-values
bird size, number, and heat production
lighting system details
maximum expected outside temperature
maximum desired inside temperature (typically 85 F)
Outputs (english and metric units):
Total heat gain through each building surface as well as the birds. - graphic.
Breakdown in percentages of various heat sources in the house - pie chart
Minimum tunnel fan capacity required to maintain 5 F differential betwen the pads and the fans
Approximate number of tunnel fans required
Average air velocity obtained with minimum recommended tunnel fan capacity.
Evaporative cooling pad area
Number of side wall inlets
You can change the minimum required tunnel fan capacity and the spreadsheet will calculate the pad to fan temperautre difference.
It is important to note that t he spreadsheet determines the minimum amount of tunnel fan capacity required to maintain at most a 5 F temperautre difference between the inlet and fan ends of the house. Additional fan capacity is often required to increase the velocity to produce sufficient bird cooling.